2009 International Residential Code. got 4 townhouses with common walls between, rated as required. roof is concrete, so no parapets required. but we have landlocked clothes dryers that would want to vent thru the roof. tried to find a minimum clearance to the common wall between townhouse units, but don't see it in the IRC. did i miss it? appreciate any help. thanks!
I don't see a specific distance mentioned in the IRC, but the IBC does mention that openings are not permitted within 5'0" of the rated wall when using one of the exceptions for a parapet (2009 IBC 705.11). Hope this helps
When you block a person, they can no longer invite you to a private message or post to your profile wall. Replies and comments they make will be collapsed/hidden by default. Finally, you'll never receive email notifications about content they create or likes they designate for your content.
Note: if you proceed, you will no longer be following .